Having problems with your Air Conditioners ?
Blower fan motor wont start on carrier package unit air conditioner I have a Carrier 50ZPA042-301TP package unit
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Blower fan motor wont start on carrier package unit air conditioner I have a Carrier 50ZPA042-301TP package unit
... Air Conditioners
The fan on my Carrier central air conditioner a/c model 38ER036300 does not move when the compressor kicks on. The unit will heat up and then will start. It also will start when I give it a small push. The 30 amp circuit breaker will also vibrate for about 4 seconds and then will be fine. Should the fan blade move freely when the unit is off? It seems to have resistance. Does it need lubrcation or is it a sealed bearing?
Hello YES the blades have to move freely.If it has oil ports look on the side of the motor for a YELLOW plastic plug/cap there are 2 one at the top & one at the bottom.Pry them off/loosen with a small screwdriver & squirt #20 oil in the holes ... Carrier 38BRC060 Air Conditioner
The fan on my Carrier central air conditioner a/c model 38ER036300 does not move when the compressor kicks on. The unit will heat up and then will start. It also will start when I give it a small push. The 30 amp circuit breaker will also vibrate for about 4 seconds and then will be fine.
Hi,\015\012The capacitor that gives the fan motor the "kick" to get it started is bad...that capacitor is localed in the electrical compartment and is often a dual capacitor with the compressor. If there is only one cap in there iwth three term ... Carrier 38BRC060 Air Conditioner
My Fujitsu Converter Air conditioner is not working... The Green light is flashing 13 times - the red light flashes continuously very quickly. The fan does not commence at all and therefore no heat or cool air comes from the conditioner at present. Also, once I press the start button on the remote control unit and the light being to flash, I am then unable to stop the unit - even after pushing the start/stop button - the lights continue to flash. Is there something I can do to make the air c
... Fujitsu Air Conditioners
I have a Duo-Therm RV Roof Air Conditioner Model 57915.622, Prod # 991731648, Ser # 84818800. It will not run. I changed the Compressor and Fan start capacitors. When I turn the unit on at the Thermostat nothing comes on. The Air Conditioner Control Unit E155095, Part # 3107541.009. The fuses are okay.
... Dometic Rooftop RV Air Conditioner
We require condenser fan motors for Interclisa Carrier package (rooftop) air conditioner model AAD 250 (1980's model) model. Air conditioner - supply voltage 380 Volts 50 Hz AC. Condenser fan motor voltage 220 V0lts 50 Hz
Hi, this is an odd voltage 380 volts. Is it a 3 phase unit? To get a 220 volt 50hz condenser fan motor, you will have to go through a refrigeration/air conditioning parts house and order this. 60hz you would have no problem finding one in stock. Carr ... Carrier Air Conditioners
I have a Friedrich 13,500 BTU WallMaster. The air conditioner stops generating cold air and seems to use the fan only on a regular basis. The front panel shows that the unit is still in cooling mode but the the unit just blows out warm air no matter how low I set the temperature. Then out of nowhere the unit will start cooling again. I know the problem is not the filter. Does anyone have any ideas? Thank you.
I'm having the same issu!!! It's horrible! ... Friedrich WallMaster WS07A10D Air Conditioner
Hello i have Carrier Weathermaker 38tkb air conditioner unit. It's about 6 years old and when i got home today, the unit itself wasn't working. Although the blower fan in the furnace inside was blowing, the fan on the a/c unit outside was not moving. I can hear a humming sound coming from it and once in a while, you hear it trying to kick in (the lights in the house even dim a bit, which is unusual), but it never kicks in. The top center of the unit is extremely hot to the touch. I've checked
The humming noise and dimming of the lights is an indication something in the outdoor unit is locked up or has failed.Check the capacitor as it may have gone bad. If the capacitor is good, then you either have a failed motor, a failed co ... Air Conditioners
I have a Carrier 5 ton Air Conditioner -five years old. I turn on the thermostat and the blower comes on in the house then the compressor engages, but the fan does start. I can manuelly, start outside fan by using a long screw driver to turn the blades. Then the fan begins to turn slowly until it reach a faster speed. But I do not beleive that the fan is turning as fast as it use to. I go back into the house and after 15 to 20 minutes the temperture has not dropped. It apprears to stay a th
... Carrier 38CKC030 Air Conditioner
Have a problem with my Intertherm air conditioner not coming on so I put a new thermostat on it. Nothing comes on fan nor heat nor air. I reset the breaker but still nothing and the unit model is a E1eb015ha? Anyone know if there is a reset button on the unit or where I can start looking to see if there is a problem.
Turn the thermostat off and check for 24vac between R and C on the thermostat. If there is no C then to G or W. If you don't have 24vac go the transformer and check for 24vac on the secondary. If it isn't there then check for 120vac on the transforme ... Intertherm P3RA-048K Air Conditioner
CARRIER AIR CONDITIONER/HEAT PUMP PROBLEM WOULD NOT RESPOND TO THERMOSTAT. UNIT IS AT LAKE HOUSE WHERE WE DO HAVE BAD STORMS. IN CHECKING, INSIDE PART OF UNIT HAD BURNED UP THE TRANSFORMER BUT NOT BLOWN THE FUSE. REPLACED TRANSFORMER . . . COULD SMELL AND THIS TIME TRANSFORMER STARTED TO MELT AND BLEW FUSE. SOMETIMES THE FAN WOULDN'T EVEN COME ON WHEN JUST SWITCHED FAN "ON" AT THE THERMOSTAT. QUESTIONS: WHAT WOULD KEEP BURNING UP TRANSFORMER. WE REPLACED WITH EXACT TYPE THAT WAS ORI
What I have always been told is if your 24 volt side burns out check the high volt side if the hi volt side burns out check the low volt side.A quick way if the primary side is burningout due to a problem with the low volt side:1 MA ... Air Conditioners
My air conditioner will not run, the fan will not run in auto or in run mode, the compressor will not start. The thermostat clicks on but the air unit does not. this is a Goodman cplj18-1b unit.
Hello, if the outside unit is not running check tje power supply to make sure you are getting 240 volts, also make sure the contactor coil is receiving 24 volts, if you are not getting 24 volts at the contactor then it may be a bad thermostat, contro ... Goodman Air Conditioners
I have a Carrier 38CKC036 Air Conditioner Unit. When I turn the thermostat on cool the compressor comes on but the fan on th unit clicks like it wants to come on but it dont. Could the fan be bad? What do you think the problem is?
Hello, this is one of 2 items...the motor itself, or the start capacitor. The capacitor is responsible for boosting the motor to get it started. Follow the wires from the motor and they will lead to an oval or round cylinder. Check the cylinder f ... Carrier 38CKC036 Air Conditioner
I have a frigidare FAM157S1A Air Conditioner, when plugged in the fan blows air but not cold air. Compressor not working, I pushed control panel to cool air, blows cold air for a few seconds, then unit blows the breaker. How do I fix it. It has been only used for two weeks and this started.
Your compressor motor is no good Time to replace unit ... Frigidaire FAH085N1T Air Conditioner
Tempstar 5000 This spring I turned on my air conditioner for the first time and it would not start at all... The fan did not turn on either. I turned off the main 220A breaker and puller the control fuses and put everything back and the unit started working fine. now fast forward to yesterday... house started feeling warm so I did the same thing... Tripped the breaker. Pulled the control fuses, and this time made sure I had new batteries in my thermostat. Started to work again. All was good. pus
... Air Conditioners
Maytag Air Conditioner Model# M6Y14F2B - unit has started changing set temperature by itself. Example: set at 72°, will hear unit beep (sometimes once othertimes several over a few minutes) and when checked temp has been changed to higher temp according to how many beeps. Have had this window unit for about 3 years and this is the first season it has ever done this. It happens randomly and on all mode and fan speed settings.
... Coleman Air Conditioners
Fan motor of my Panasonic room air conditioner outdoor unit, model # CU-XC93KP, serial # 0567000375 is starting to make some noise, I would like to have the fan motor replaced but cannot get the part (catalog) number of the fan motor. Regards, Luis Vander-Linden
Do you know a service tech? Wholesale houses have generic motors for these now at about 1/3 less then normal price. Warning be prepaired to pay a higher then normal price due to the copper shortage... ... Air Conditioners
My air conditioner is blowing warm air in the house and cool air outside. The fan outside was stuck and not spinning so I gave it a nudge to get it started now the unit seems to be running in reverse.
You will need to replace the fan motor. Basically when the system starts running in reverse the fan motor is shot, and the electrical is telling to motor to spin one way but since the winnings are shot then are making the motor spin the opposite dire ... Whirlwind FH-778 Air Conditioner
When calling for cold air, the fan in the cooling unit hums, but does not spin. With a nudge, the fan does spin. Looks to be smooth and normal speed. However ambient outside air 80 degrees. the air through the register is 72 degrees. Is there a switch that will not allow the fan to start on its own if the coolant is too low? Do I have two problems, fan starting AND insufficient cooling? Unit worked well the last two days.
Sounds like start capacator possibly bad ... Air Conditioners
The AC unit turns on and I can cycle through the options in order to adjust the fan speed however the fan does not start in any of the three settings. The ac unit produces cold air, however the fan does not run. The unit sounds like it trys to get the fan to start however instead of blwing air it produces a funny smell. Any suggestions?
You say the unit produces cold air ??? where are you getting the cold air from???\015\012If your fan does not run in any speed F1, F2 F3. and a funny smell sounds like the motor is bad\015\012Mine works in F2, F3 but not in F1 ... Kenmore 75085 Air Conditioner
I have a Carrier Air V air conditioner on which the compressor won't start. You can hear it try repeatedly, but no luck. The fan does work.
CHECK AMP DRAW IF ITS HIGH BAD COMPRESSOR WINDINGS, MAKE SURE YOUR GETTING PROPER VOLTAGE DOES CAP HAVE A RUN AND START SIDE CHECK BOTH. START CAP COULD BE BAD. ... Carrier Air Conditioners
My air conditioner stops cooling. Occasionally, it will just function on fan mode even though I confirm that it is on cool mode. Warm air comes out even on the absolute coldest setting. I have to turn it off and use the manual reset button on the plug to get it to work properly. The problem started after the unit iced up one night and it hasn't worked right since. Is there any way to fix this or am I gonna have to get a new AC?
If after reset the A/C cools then the fault seems related to the thermostat or the cut off pressure switch or load cut off.\012However is there is no cooling at all the compressor and the gas pressure- check for leak if gas is absent.- must be ... LG ZW6500R Air Conditioner
GE Air conditioner wall unit started on 7.19.10 stopping for no reason, continued stopping on 7.20.10 like 3 times (10.40 p.m. and 2 times after that) and had to reset a/c; 7.21.10 a/c stopped at 10 p.m. - reset a/c and today, 7.22.10 NO COOL AIR at all! The fan feels cooler than the A/C. What's up with that?
... GE APN08AA Portable Air Conditioner
I have a carrier 38ckc030 air conditioner. the unit outside is not turning on. it sounds like it wants to and if you manually spin the fan it will slowly build up speed, but the air coming into the house is ambient temp. I searched and it sounds like the startup capacitor might be the culprit. Any advice?
You are right replace the compressor/fan capacitor this helps compressor/ fan start its the round silver or oval part in the condensor ..let me know ..good luck/joe/ ... Carrier 38CKC030 Air Conditioner
I have an Armstrong package unit gas heat and air unit and the fan started blowing all the time and it will not shut off
Does your heater work otherwise or is it just the blower going non stop? I have worked on a few armstrong brands but they weren't a big seller in this area. However general electric units had a fuseible link located close to burner compartment. This ... Air Conditioners