Having problems with your Air Conditioners ?
I have a ruud furnace/airconditioner Model:UGPN-07EAMER, Serial: FU5D302F390401344. When the thermostat calls for heat, a little motor (within the furnace itself) or something kicks on, the burners ignite a few seconds later, then the blower starts. It's at this time the flame goes out and the blower is just sending cold air throughout the house.
There are two green lights (power and ok) lit normally and the
orange(ish) blinking "flame" light on the main board. When the flame goes out, the
Hi, this motor is the inducer motor, which is the first thing to start on a call for heat. Everything seems to be going through its sequence of operation just fine, but then shutting down on a safety. Look on the panel for a chart that should tell you by the number of flashes and color of the leds what is wrong. It is locking out for some reason, could be several of many. Next to the pilot, you will have a flame sensor. The metal tip sets in the pilot flame. When they get dirty, they will cause the furnace to do just as you say, run and then lock out. You can take a piece of sanding cloth and sand the metal tip on this flame sensor. If this is the problem, it will start and stay running. Also, look for this chart I have told you about, as it is there to help you locate which safety is giving you the problem. My bet is the flame sensor. Please keep me posted, and rate me on my help to you. The flame sensor also has a electrical lead that is attached to it going to the board, so you will see it.
A/C, & Heating Contractor
A/C, & Heating Contractor
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
I have a ruud furnace/airconditioner Model:UGPN-07EAMER, Serial: FU5D302F390401344. When the thermostat calls for heat, a little motor (within the furnace itself) or something kicks on, the burners ignite a few seconds later, then the blower starts. It's at this time the flame goes out and the blower is just sending cold air throughout the house. There are two green lights (power and ok) lit normally and the orange(ish) blinking "flame" light on the main board. When the flame goes out, the
Hi, this motor is the inducer motor, which is the first thing to start on a call for heat. Everything seems to be going through its sequence of operation just fine, but then shutting down on a safety. Look on the panel for a chart that should tell yo ... Air Conditioners
My mother has an intertherm furnace that all of a sudden started to throw cold air. When we restart it, it will work for about 20-30 minutes then the flame goes out and only blows cold air.
... Air Conditioners
Weather King 10AJA3001AH Air Conditioner Heater if the heater has been off all day i come and turn it on it works fine but when it comes on again it only blows cold air the burners will fire for about 2-10 seconds right before the blower comes the fire goes out it repeats this for about 5-6 times then it just goes off, how can i fix this problem
I think from the erratic way that your furnace is functioning that you will need to replace the control board to solve this problem. Ihave had this happen several times and I would recommend that you check all connection on control board,gas valve ,i ... Weather King 10AJA3001AH Air Conditioner
Heater,.... AC sends warm air when needed, but changing over time, as now that is hot outside, the cold goes well, for a while, after about 30 minutes, the AC is freezing the two tubes into the external, covered with a rubber one black and one color and thinner copper. same thruster so that is on the outside of the house as it happens ... inside and outside the tubes ... I repeat that the air is going well but then it freezes it does not, therefore I can I do? manually turn off the breaker box.
First check your air filters and make sure the inside and outside coil are clean. If they are clean and you are getting good air flow over the coils then you probably will have to get the unit charged. ... DeLonghi Trane 5t Rooftop Air Conditioner Ycy060g1m0ad
When I set tstat to call for a/c, compressor outside comes on. Blower on furnace does not. When I manually rotate fan limit switch on furnace wall, blower comes on, blows cold air, and then goes off when I release the fan limit switch. I have a Honeywell 83251008a low and high voltage transformer, and Honeywell (I think) limit on off switch. I also noticed the 2 wires coming from the Honeywell Gas regulator are off. They were connected at the onset of the problem. I am not sure where to re
Sorry, you mean gas valve control? when you have only 2 wires, usually it doesnt matter which terminal as there,s no polarity differentiation at that locationYou should never rotate this dial by hand, you will bend the helix inside and fan will not o ... Air Conditioners
Yes the flames do stop but the blower continues to run blowing cold air. I have to push the reset switch in order to relight the flames. Is this switch bad? It's a Carrier model, 58SXC. If it needs to be replaced, can I change it myself? I'm handy. And I can get to it.
Hi; Where is this reset located please be detailed as possible. maybe the switch is good I think You need to watch operation very carefully...alpharome416 ... Air Conditioners
Luxaire by York Furnace,Model# G8T10012UHB11A,8 Red LED Flashes = Ignition lockout due to recycles,Has flame for a few seconds then goes off; does it around three times,Fan is working; blowing cold air
WHERE CAN I BUY REPLACEMENTS PARTS FOR THE SAME MODEL #\012G8T10012UHB11A ... Coleman Air Conditioners
My American Std/Trane heat pump model#WCX036A100BB keeps freezing up at the internal coils & compressor tubes. I had someone out the other day, who topped it off with R22. It wasn't that low, according to him. I have cleaned both the inner coils and the external. It is a package unit, so essentially both are external. But I am referring to the coils that the return air goes through (same compartment as the blower fan). It still blows cold, then freezes after a couple hours of running. Chec
... Air Conditioners
Hydroflame 8241, ignitor has been replaced and still get a big boom when lighting. after a $160 bill the boom continues and flame goes out after 5 seconds with fan continuing to blow cold air for a long time. Trying to solve before deer hunting! HELP
Http://bryantrv.com/docs2/docs/hflameservice.pdf ... Air Conditioners
My furnace will ignite then after about 3 - 5 seconds it goes out and blows cold air, I was told it was the flame sensor, is that what it sounds ike to you
That is a good possibility-- Did you try cleaning it- and making sure the wire is tight from the Flame rod, thru to the circuit board it connects to.What type of ignition?-- Glowing ignitor?-- Is it nice and bright, and the correc ... Air Conditioners
Pilot will go out, blower will continue to send out cold air, temperature will drop almost 20 degrees. The main switch will have to be shut off to turn the pilot back on, but it takes hours to come back up to temperature
The system is going in to lockout due to ignition failure. A couple of things to check: First the filter.second there is a rubber tube coming off of the little blower that's about at waist level on the furnace(If it's a standing furnace) remove the h ... Air Conditioners
We have a Vulcan ducted heating unit model HX100, recently we have experienced problems with the unit where is it not heating the house, the unit goes on but blowing cold air. We have had a couple of technicians to repair it and still not working. One fixed the switch pressure & the other the flame sensor connection. We have been advised that we may need a new unit or repair the board. As we have an illness in the family, we would like to know whether we need to purchase a new unit as p
\015\012We had the same problem with our carrier heater 4 year or so ago. We had a technician and electrician try to resolve the problem. What the tech suggest was to replace the main component ... Air Conditioners
I have a Procom MN300TPA and I used it all last winter with no problem although it was very noisy. This winter I used it twice and had to turn off the gas and now the pilot wont light. I hold the button down and the pilot stays lit until I turn the knob to on position and it immediately goes out. I changed the thermocouple (guy at LOWES sold me a blue flame thermocouple) , have blown out everything you can with air compressor and it still wont work PLEASE HELP it is getting cold here, only sourc
Hi, make sure the fitting at the gas valve for the thermocouple is tight, and the other end is in the flame good. Also, make sure you have a nice blue flame surrounding the tip of the new thermocouple.You have a small screw on the valve that says pil ... Air Conditioners
I have a Carrier Gas Furnace Model # 395CAV024055ABJA, I works fine if you keep the temp low, like 68, so that it doesnt come on very often, but if you try turning it up and it needs to run for awhile, it wil start this cycle where the flame will kick on and off, the blower is continously running and only blowing cold air, I have tried new batteries in the thermostat on the wall, and have tried putting it on manual heat, no change, another thing is that once it starts this cycle, if you shut it
It sounds like it is going into overheat mode. Check the overheat sensor, make sure the flue is clean, make sure any filters are clean, also check the gas passage inthe heat exchanger, if there is a blockage from soot the system will overheat ... Carrier Air Conditioners
I have a weather king model 90RJ - first time I've had hot air heat..When I turn on the heat, the blower turns on right away ( blowing cold air) - I understand that the ducts have to cleared of the cold air - but shouldn't the blower turn off until the air is warmed to temp thanks Bob
When the furnace first comes on there is a induced draft motor that should come on first but that forces air up the exhaust or flue,not into supply air on ductwork. It is not unusual for cold air to be blown out when burner first turns blower motor o ... Weather King 10AJA3001AH Air Conditioner
My air conditioner delivers cold air only in spurts. It then goes into fan mode for a few minutes, then to cold air in a few more minutes. It is over 100 degrees outside and the inside of the house is 85 or so. I have the temperature set at 74 degrees. Why does the cold air not pump out consistantly?
Hi,The\012 unit is probably low on freon and so it is running too cold....this \012trips the freeze stat and shuts down the compressor till it warms up The unit will \012need to be recharged or replaced...\012Here is a t ... Fedders AED24E7F Wall/Window Air Conditioner
I am looking to buy a house in forclosure. It has a Tappan gas furnace about 9 years old and there is no manual. Can you advise as to whether the following problem is serious and estimate what the cost of repair will be? Exhaust blower is always on; red light on circuit panel is constant. Then gas flame is ignited and burns for a couple of seconds; yellow light on circuit panel comes on. When blower motor begins, gas flame goes out, yellow light goes out, and red light repeats sequence of 2
HelloSounds like the flame sensor is bad.Or possible photo eye.Worst case would be a new circut board.Anywhere from $100.00 to $300.00 depending.Legally a home you purchase has to have a heater that works and a hot water ... Air Conditioners
Blower motor my air conditioning goes off as soon as it goes on I have a service contract with my local oil company and my repair man said I need a Bryant blower motor 8539DL 51923EEOS I have been told the part is not available because the unit is to old and they recommend replacing my furnace and air conditoner for over $15,000 I am hoping I can buy the replacement motor somewhere so I can save for the future replacement of my units Is this part available anywhere?
YES!! A universal replacement is readily available for around 200$ or so and the labor for the installation should be about the same. Sometimes it's hard to tell the Tech's and the Sales apart....GL! ... Bryant Air Conditioners
2002 GMC Sierre Crewcab 4x4 Duramax Diesel A/C problem on 2003 duramax, air blower blows but air is not always cold. Often starts blowing cold air but the air gets gradually warmer as if AC is not on. I can actually turn AC off and circulate air in cab and get cooler air that way. It has been checked by gauge to have plenty of coolant.... any suggestions for testing compressor or another part?
Ok now you said,the system was checked to be sure the refrigerant level was full . It could also be over full causing a over preasure shutdown. The compressor has a low and high pressure switch, that will disengage the compressor clutch if it senses ... Air Conditioners
No cold air coming out of blower
They can be recharged using a piercing valve like this.\015\012\015\012 ... Air Conditioners
Warm Air My Fleetwood motorhome Dash air is giving me problems. After I turn on the controls Blower, outlet position, AC on button and re circulate button I may or may not get cold air. After continually operating the controls mainly blower & AC button, I can some times get the AC to cool down. When it is warm it's about 80 degrees, when I do get it to start cooling it will go down to about 60, Checked with an IR thermometer at the vent. Once it does cool down it may work the remainder of the d
... Air Conditioners
Hi I have got adouble storey house. I have moved into the house this year. My Fujitsu ducted air conditioner is not cooling well. I think the blowers are too slow. My model number is AOT60RPAGT. Cooling in downstairs is ok but upstairs in the bedrooms it is not good. When I put my hand close to the vents I can feel a bit of cold air but I think the blower is too slow. I have selected blower speed to max on the control panel but still it doesn't work satisfactory. Please advise. Thanks
... Fujitsu Air Conditioners
I have a GE ZONELINE 5100 hvac unit when unit is turned on the blower works but it will not generate heat when set on heat selection nor will it blow cold air on cold air selection it just blows air out like normal fan what could be the problem
Check the selector switch to make sure that the controls are transferring from heat to cool. Then if the control is working you would have to check power to the valve that changes the flow of refrigerant from heat to cool. This unit may be heat ... Air Conditioners
At 30,000 miles my then 8 or 9 month old chevy 2500hd 4wd pickup truck air conditioning started blowing hot air on the driver side (the passenger side was still cold). I turned the truck off and back on and it began blowing normally for a few days and then it would do it again. A year or so later the heat on the driver side went out totally (passenger side worked properly). So now the driver side blows cold air constantly. A few months after that the blower quit working all together. Now at 185,
What year truck is this? This is actually a very very common problem on those chevy trucks. Most times it is the door blend actuator that has failed. and the default for this failure is driver side blowing hot. There are a million posts out there on ... Air Conditioners
I have an older Carrier Gas Furnace. I can't read the complete Model number. But since Thursday morning, the blower just keeps blowing cold air, the spark igniter won't spark and the air damper will not open. I replaced the spark igniter and the pilot assembly for $215 and the thing still just won't light. As soon as you turn on the power the blower comes on and just runs. I check my 24v supplies from the transformer, and I am getting voltage. What else could it be. There are no LED's on the PCB
Nothing will happen until the draft motor come on or the vent damper opens. if that's happening, are you getting gas? ... Air Conditioners