Having problems with your Air Conditioners ?
My Soleus KFR-18GW Split System Air Conditioner cools fine and heats good but the fan would never stop running
Check your thermostsat see if there is a fan switch on it set it to auto
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
My Soleus KFR-18GW Split System Air Conditioner cools fine and heats good but the fan would never stop running
Check your thermostsat see if there is a fan switch on it set it to auto ... Soleus KFR-18GW Split System Air Conditioner
Model FC24B3XN1H. Modulating Echelon 60k btu. Fan runs constantly but no heat. Was installed 9/09. When turn thermostat off, fan still runs, have to shut off at furnace. It has never been a hot heat, installer said that is normal?? Used air couple days this week, was fine. We then turned furn off at thermostat as it was not needed. Turned heat on late yesterday afternoon & problem started. Left furn power off for about 15 minutes, but would not reset. Easy solve?? Is it supposed to be a 'cool' h
Hi,The fan running constant and the unit not firing is usually an indication that the high limit reset has tripped. And yes... these furnaces will run a cooler air... that is one way they get better efficiency...Also the ... Coleman Air Conditioners
I have a Nordyne Intertherm split system Model MMHA-056ABHR-01. The blower starts and stops or oscilates when trying to heat. The burner ignites fine and the fan will run fine when put on continuous. But when the thermostat is set to auto and calls for heat the blower starts then stops.
... Intertherm Air Conditioners
My LG LST244M split unit will run for a couple of minutes, then the condensor fan will stop and the condens will heat up and because of that the compressor will stop, why would the condensor fan stop?
Couple of things to check. 1st the capacitor for the fan may be going bad in which case the capasitor will need to be changed. 2nd. the windings on the motor may be going bad. The windings, if they are bad, swell putting pressure on the motor causi ... LG Air Conditioners
I have a Dometic 15,000 btu, ducted air conditioner in my 30 ft fifth wheel. It seems like the unit has never cooled very efficiently. Dealer has checked out. I noticed yesterday, outside air over 100 degrees, that the air conditioner would put out good flow of cool air, but once in a while compressor would stop running even though not close to thermo setting. Fan would continue running. Any suggestions?
Not sure what the pressure sensor should ohm at but i would suspect a faulty sensor if everything else checks out. Its very common for these sensors to exhibit issues when they get hot. Also you may have a filter in the system that may be restricte ... Dometic Rooftop RV Air Conditioner
I have a 2 year old Duo Therm 15,000 btu Heat Pump AC unit in my RV. The compresser will not come on or even try, in either cool or heat mode, the fans runs in either auto or on position. I have a wall thermastat, all wires & connections at the thermastat and the controll box look good. The units was running fine, with no prior symptoms and then it just stopped cooling. I have a strong electrical background with all the meters, I am just not famaliar with RV AC units. Bud De Fore don
Hello Bud,First of all, is your wall thermostat a digital thermostat, like a 4 or 5 button Comfort Control Center? Is the ambient temperature under 40 degrees?Is your fan still able to run, are you able to control ... Dometic Rooftop RV Air Conditioner
Hi my name is Tony and i attended a site with a sharp wall mount split, don't have indoor details but the condenser is a AE-X099E R22 unit. the problem is that on heating the system works fine for about an hour then the indoor fan stops and the yellow light flashes on and off at the same time the compressor stops and the outdoor runs for a while before it stops. any ideas.
... Sharp Air Conditioners
Hi the outdoor unit turns on ( fan runs) the indoor unit does open, no heat or cold air blowing. In just fan mode the unit works fine etc speed setting ok. Its a sharp split type air model # ae-a244j outdoor,ay-a244j indoor unit what would be the problem, theres only two parts in the outside unit behind the side plate where the wires info is,small black box three wires and a round unit with wires. I hope this is help full cheers andrew
My gut says that this is evidence of a bad control board(circuit board). As usual, double check that your batteries are good in the thermostat. I have seen some weird things happen when the batteries are low. This one may be a job for your local con ... Sharp Air Conditioners
Have NEC RIH-2667 Inverter Split system.I set to Heating mode,set temp to 25 degrees.The compressor light comes on.The run light flashes for about 30 seconds.Then the vent opens,the fan comes on and starts blowing out heat.Within 5-10 mins the temp on split displays starts going up.when it gets to 26-27 the run light flashs,fan stops,no heat coming out.The temp on system keeps going up to 30 degrees.it takes approx 40-60 mins to come down to 25ish the will come on again and repeat.I have an inde
... Air Conditioners
Lg lsu242he a/c runs fine but when unit is in heating cycle ,the fan wont stay on.fan came on a split second then cut off.outdoor runs fine in both heat and cool.LCD seems like it is fluttering in this mode as well.checked defrost sensors and they both are open.
Hi, whenever this type of problem is exhibited, usually we suspect the thermostat itself, as this is what ultimately controls the fan.\015\012\015\012It still maybe a sensor, (the ONLY way to tell is by substitution with a "Known Good") althou ... Air Conditioners
I have a Arcoaire Gas Furnace (Model# GNJ100N12A1), that will not fire up. It has a White Rogers Digital Stat. First the Stat seems to be faulty, since it reads 70plus in a house that has a temp of 30 or below. I can adjust the Stat and the blower motor will run. The rollouts (3) were reset; the inducer fan would run; then the unit would cycle and shut off. Now the inducer won't run. The ignitor is good, but would never glow. A friend tested the current coming from the Stat, and found 24
Sounds like a faulty board. shut the power to the furnace off for a minute then turn it back on. Make a call for heat at the thermostat. The inducer should start and close contacts on a pressure switch . Once pressure switch closes the hot surface ig ... Air Conditioners
Ihave a Day & Night Furnace M/N:58GS050-3 Series 301 S/N:Z33A65482. My problem is with no wiring whatsoever landed @ terminal strip fan runs @ high speed constantly.With stat wired up & a call for heat I get no spark,just fan(fan switch -auto). 24vac is present into circuit board from transformer, but drops out to 15.xx @ R & C.If I apply 24v directly to R along w/other wiring,fan stops,but after ignition main burners light,fan never runs.
... Carrier Air Conditioners
My indoor unit on my heat pump will not shut off. The electric heat keeps running, and the fan keeps running. It only happens when it is really cold, like 25deg or below, above that and it functions fine. The outdoor unit shuts off, but the indoor stays running. I do HVAC work, but I have never seen a problem like this. I have switched the stat out, and its just so strange. I figured the relay may be stuck, but if I turn the stat off, it turns off shortly after which tells me it may not be the c
I would venture to say your stack relay is getting stuck. either that or you have a short in your low voltage wiring somewhere that is not always making contact....or it may be making contact through another median...like ice or frost. Remember ele ... Intertherm P3RA-036K Air Conditioner
My central ac unit never shuts off, the fan blows all the time (the compressor comes on and cools good, but the fan never stops running)is this normal?
No..check the fan relay/board ... Whirlpool ACQ122XK Air Conditioner
3 new Coleman 47073-879 ac units don't shutoff cleanly. 2 have heat pumps and they change fan speed quickly when starting and stopping. I've never had heat pumps before but find this start and stop sequence annoying. This is a brand new coach so I expect any needed service would be covered by warranty.
... Coleman 13.5 Btu Rv Air Conditioner
Hi, I have a LG NEO PLASMA S18AHN SPLIT UNIT, It was already installed in our house upon us purchasing it, it would be approx 3 years old, has been pretty much running 24/7 and has been great up until recent, about 6months ago it stop and displayed the C6 error code, at this time I replace the external units motor start capacitor, it ran perfertly again for the next 4months, until it stopped again and again after reseting. When trying to run on Heat it comes straight up with "Defrost Mode" it
My lg 18 000 btu split neo plasma is on heating in any mode u put it\015\012what do u think is the problem ... LG Air Conditioners
12 year old Amana Heat pump stopped cooling and heating. The compressor was replaced, the fan motor, etc. AT first it would run for 15 minutes and stopped. The repair person returned twice and the thi
... Air Conditioners
No Heat I have Comfort-Aire EKTC15-150B and the heating element is not coming on. The Fan will run but we do not get heat. We had a power outage and it was about the same time the heat stopped working. Is there a manual reset or fuse that needs to be change? Any help would be greatly appreciated it's cold today. Thanks
I NEED TO KNOW IF THIS IS A SPLIT SYSTEM ONE INSIDE ONE OUTSIDE OR IF IT IS A PACKAGE UNIT ONLY ONE OUTSIDE OR IF IT IS A WINDOW UNIT SELF EXPLANITORY?\015\012IF YOU GIVE ME THIS INFO I CAN HELP YOU ... Comfort-Aire EKTC12-150J Air Conditioner
I noticed some straining noise coming from my a/c unit today. The fan on top of the condenser runs fine but as soon as the compressor tries to kick on the fan stops for a split second and you get a kind of surging noise from the condenser unit. Then the fans kicks back on, the the process repeats itself every couple of minutes. Meanwhile no cold air is being produced inside the house. Any ideas?
You amy ahave a bvad capacitor on the outside unit. It starts the fan and the compressor. You can change this yourself. Open the outside panel and you will see a silver canister with terminals out the top. Replace this and I think your problem will g ... Goodman CKL24AR24 Air Conditioner
My Ruud heat pump fan stops after running a minute. It is 10 degrees out now and defrost mode seems to work fine. It makes a humming sound when the fan gets stuck. Sometimes if I take a ruler to it, it will unstick and starts spinning but not other times. cover over the fan motor feels very warm, almost hot to the hand. I've shut it off totally for now.
Hi,The capacitor for the fan motor is bad...replace the capacitor and you'll be good to go...\012Here is a tip about troubleshooting your air conditioner...\012There are many things t ... Ruud UBHC Air Conditioner
Heat pump fan will not stop running
Could be a heat sequencer. if the stat was bad it would run constantly in both modes. ... Air Conditioners
Please help, I've just installed a split and the head unit blew warm air for about twenty mins and the outdoor unit would run for about 1min intervals. After 20 mins it stopped all together then the heating led would flash twice followed by one flash of the cooling led. I tried to shut down and reset but had no result. Any ideas ?
Try to check the program on the remote, together with electrical connection and the refrigerant charge if if ok. also check main breaker. ... Air Conditioners
My split system runs for about 8-10sec and is cool. It the stops and starts again for the sane time and again and then shuts down. It dies the same on heating and cooling. The fan in the compressor is running normal and is not struggling. I have checked the filters and have cleaned them, still no joy. Please can you advise me what else to do. My ac model is cs-a12ckp Regards Nicks
Simple- Short cycling : Check coil and room sensors. Misplaced or fell down. Fix in right position. ... Panasonic Air Conditioners
Hi. I recently installed 1.5 T, 3 * Split AC, LG. Whole day the AC works fine and no problem in cooling too. But once in 2 day outdoor unit start making thudding noise continously and does not stop for 4 to 5 second and after that indoor unit stops cooling and just fan runs. No cooling is done after that and room temperature keep increasing. The green LED of compressor in indoor unit is ON, compressor does not work. To achieve cooling again I have to switch off whole unit for like half an hour a
HelloSounds like the compressor is shuting down on high heat.There could be a couple reasons for this.1 Check that proper voltage is being supplied to compressor.2 Freon level may be low.This would be a service call.3 Ba ... LG Air Conditioners
My Carrier Tech 2000ss.The fan on the unit outside runs continuosly.The heat and cold work just fine,but the out side fan never stops.I was told ,that it is probably a relay switch.Tell me what you think.
Sounds like the fan relay is stuck and staying on so that the fan continually spins. Pretty common issue and shouldnt be to much for a tech to replace. If you do the job, just make sure that you get the right part. Parts house will need serial and mo ... Carrier Air Conditioners