Having problems with your Air Conditioners ?
I am replacing a White Rogers 1F58-77 with a Honeywell RTH2300. When I removed the old stat the wire colors are white, red, orange, green, yellow, and blue.
G- green wire
Y- Yellow wire
R- Red wire
W- White wire
X1- Blue wire
I hooked up all the wires except the blue. Instructions with the Honeywell unit said not to hook up the blue wire if there is an orange wire to hook up which I did.
The problem, when I light off the A/C (heat pump) the compressor comes on but the
Yes you did correct. Tape of f blue wire. On your thermostat you should have el/gas turn top el and fan should work Russ
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
I am replacing a White Rogers 1F58-77 with a Honeywell RTH2300. When I removed the old stat the wire colors are white, red, orange, green, yellow, and blue. G- green wire Y- Yellow wire R- Red wire W- White wire O-Orange wire X1- Blue wire I hooked up all the wires except the blue. Instructions with the Honeywell unit said not to hook up the blue wire if there is an orange wire to hook up which I did. The problem, when I light off the A/C (heat pump) the compressor comes on but the
Yes you did correct. Tape of f blue wire. On your thermostat you should have el/gas turn top el and fan should work Russ ... Air Conditioners
I am replacing a white rodgers thermostat with a honeywell rth3100c. i have matched my wire as e (brown) to e w2 (white) o aux y (yellow) to y g (green) to g o (orange) to o l blank r (red) t r b blank c blank now i have a blue wire which was hooked up to the x1 on the old thermostat. where does this wire go?
Blue (C) or sometimes (B) should be your common wire. Look at your schematics and locate common. Your Brown wire is (E) and is emergency heat, white wire (W) is Auxilary Heat, green wire (G) is fan relay, red wire (R) is power, yellow wire (Y) is C ... Air Conditioners
I have a tempstar with 6 wires. Green, Blue, Red, Yellow,White, and Orange. I am trying to install a White Rodgers 300 thermostat and letters are not matching up. The thermostat has G, A, RC, RH, O, B, Y, and W. I don't know where to hook the blue wire which was labeled C. Unless it goes to RC and the red goes to RH could you please help? Thanks
You need to verify the function of each wire with Tempstar then cross it with the WR stat. Call the techline if you need further assistance 18002842925. ... Dometic Rooftop RV Air Conditioner
I have an older Carrier Heat Pump which I am trying to update the thermostat control with a Hunter model 44550. The problem is that the wiring to the current thermostat is as follows, G= green wire, R= red wire, W2= blue wire, O= orange wire, Y= yellow wire, E= grey wire and C= white wire. If I am reading the schematic correct for the Hunter thermostate I am to wire as follows Green to G, Red to RC, Blue to W, Orange to O, Yellow to Y/Y1, C cap it as batteries are used. It does not tell me
JUMPER STAYS BETWEEN RC AND RH SO YOU HAVE INCOMING POWER FOR BOTH COOLING AND HEATING. THE WHITE WIRE YOU SAID C IS COMMON AND SHOULD BE USED IF POSSIBLE TO COMMON TERMINAL ON NEW STAT . IF THERE IS NO COMMON, THEN CAP IT BUT YOU'LL BE CHANGING BAT ... Carrier Air Conditioners
I have a carrier air/heating unit with pump. It has 8 wires. Brown,blue, white, yellow, green, black, orange,and red. I'm trying to install honeywell thermostat. The wires from my unit are suppose to go into these honeywell (RTH3100C) thermostat slots. hONEYWELL WIRE SLOTS E Aux Y G O L R B C The only thing i have to go on is the wire colors from my wall which were not labeled or coded in any way. I am not sure about the model# of our unit because it is so old that the model# has faded away the
Turn the power off to the air handler. Open the control cover. Write down what color wires go together at the wiring terminal. All 8 wires are probably not used.\015\012Post the findings here.\015\012In most cases,\015\012E= brown-e ... Carrier Air Conditioners
Changing from a Trane Weathertron Heat Pump thermostat to a Honeywell TH5220D1003. The Trane unit had a white wire, green wire, red wire, orange wire, yellow wire, blue wire and a tan wire. Where do they go on my Honeywell TH5220D1003
... Honeywell Air Conditioners
I have a Janitrol Heat Pump Thermostat HPT-18-60 and need assistance connecting my new Honeywell RTH7500D thermostat I have a Goodman Heat Pump System Indoor Unit Model#AWB24-05C REV D Outdoor Unit Model#CPLE18-1 Here is the wiring of the old thermostat Y-Yellow Wire G-Green Wire R-Red Wire O-Orange Wire W2-White Wire E-Blue Wire C-Black Wire Where should each of these be connected to the new thermostats terminals?
... Air Conditioners
The heat strip was never hooked up, there is three wires on top of the heat strip, grey, brown, and white , the thermastat is only hooked up with green yellow and red. There are two wires not hooked up a white and blue. There is a blue that is not hooked up on the unit. this is a package unit. I know that the three wires activate a relay to turn on the strip, and the white goes to both the grey and brown relays if they are some sort of relay. So I hope you can help me. drew
Hello! Please give me the make, and model # of your unit.Guru...............saailer ... Air Conditioners
I installed a new Honeywell Programable thermostat, When I turned on the AC it turned on the Heater... I followed the wiring but some of it is not making sense... G=Green, Y=Yellow, R=Red, C=Blue, W2=White, Y2=Brown... The problem is that I have an Orange and Black Wire left over, Which one do I connect to W? and do I have the wiring right... my unit is a central Heat & Air, not a heat pump.
Hi, the problem is you have bought the wrong thermostat for the unit if it is not a heat-pump. A heat pump will have W-1, W-2 for heat strips, and Y-2 is for 2nd stage cooling. G is Green for Fan, R is Red for Power, Y is Yellow for cooling, and W wo ... Goodman Air Conditioners
I need the wiring diagram for this thermostat, there are four wires that are hooked up red,white,blue for yellow and green. They connect to a honeywell relay that has five connection, y,g,w,c,and r, do i connect them the same way as colors match
On the fan relay hook up the red to r terminal the white to the w terminal and the green to the g terminal , now the blue needs to hook up to one of the two wires going to the outside condenser unit and the other going there goes on the c terminal . ... Carrier TSTATHCP Programmable Thermostat Air Conditioner
I'm installing a Honeywell RTH7600B programmable thermostat and replacing a Honeywell T87F2873. The new one calls for a Red, Green, White, and Yellow wire, while I only have a Red, Green White and Blue. How should I connect the new thermostat?
Every thing the same except take your blue wire and replace the yellow for it. So when you hook it to t-stat goes like thisRed to R White to WGreen to GBlue to Y ... Air Conditioners
I just replace a Honeywell T87F28733844 Thermostat with a Honeywell RTH221 Thermostat since then my the furnance will not produce any heat. I replaced the thermocouple, but still no go. The pliot light is lit, but still no go. The wires that went to the T87F are yellow, green red and blue. The RTH calls for a yellow, green, red, and white, with a jumper jack in the Rh Rc. The blower for the fan works, and the ac works, but not the heater
The heat circuit uses 2 wires to the thermostat one is the power from the transformer, and the other goes to the gas manifold.\015\012\015\012The Rh and Rc is probably the power for heat and cool, and this is where the red would attach IF ... Air Conditioners
I have a Intertherm P3rA-042K that runs the ac at the same time as the heat strips. I have a Honeywell RTH3100c I have the red wire at R the Yellow at Y the Green at G and the W2 at aux. I had a jumper between Aux and E like the manual said but it makes no difference. Also for some reason it was hooked up before with a blue wire joined with the red at the unit and the blue going to B at the thermostat. I removed the blue as i saw no use for it and it still doing the same thing. The unit froze up
Red, green, and yellow should all be from AC unit. What other wires do you have there, and are they separate from red , green, yellow? ... Intertherm P3RA-042K Air Conditioner
Honeywell 7512A. Working fine. Turned off power yesterday notice no display so once power was restored I changed to new batteries. There should of been a display due to the batteries. New batteries were checked fully charged. Breakers were all reset. Batteries are in properly. Now I have no display. Polarity is correct. Wiring configurations is White to white. Orange to Yellow terminal. Green to green. Black to red terminal. Red to RC terminal. I have airconditioning and heating.
... Honeywell Air Conditioners
T-Stat Replacement I am trying to replace an old t-stat with a new Ranco ETC-111000-000. The old t-stats have no idea what they are they are old and rust can't read. The old ones are hooked up with only two wires, (where i used to work and bought these from we used 4 wires so im lost) The old one has a red, yellow, and blue dot on them. Yellow is on top, blue middle and red bottom which is common. I have a Blue wire hooked up to common and a orange wire goint to yellow dot(?) on my new t-stat wh
You will have to trace the wires from the source, unfortunately, the colors may not be accurate. Do you have a 24v heat and cool system? I am going assume the answer of yes, as this is the most common. If you have something different, we ... Air Conditioners
Wiring transformer Trying to install a transformer. The units wires are yellow, black, red and blue. The transformer has green, blue, orange,and white wires not sure what goes were. I have already burned one transformer.
You have a "Multi-Tap" transformer, and should have a white label on it with wiring. ... Air Conditioners
I am installing a Mars 1/3 hp fan motor. It has a black wire,red wire, blue wire, yellow wire and (2) brown wire that go to a capacitor. May Furnace has Black power wire, red wire (speed) and white common. What wire is the common to the fan motor?? I hooked it up with black to black, red to red, and white to the blue. It ran fine for 5 min then it thid my breaker in bresker box???? If the blue was not common how could the motor run at all??
Hello, Typically your common wire will be white, high speed- black, medium speed- yellow, medium low-blue, red- low. The motor could still run for a short time if it was wired wrong but will either trip a breaker or go off on it;s overload when it's ... Air Conditioners
I have a Trane Heater/AC unit no heat pump with a thermostat model 802AS32DAA that has seven wires. I am going to a five wire heating/cooling thermostat. What do i do with the two extra wires? old thermostat red wire-RC slot (24 V from A/C) white wire-W1 (???) yellow wire-Y (A/C Compressor) green wire-G (A/C Fan) black wire-B (?????) Blue wire-Y2 (????) orange wire-W2 (24 V to Furnace new thermostat therminals G Rc Rh Y/O W/B Y1 Can you tell me what wires to connect to each
From Honeywell : "If your old thermostat had Six or more wires, the replacement you have is Wrong!" ... Air Conditioners
I have a RUUD AC Model UPFA 060JAS, Serial # 3687 F4787 3195. My dog ripped the wires apart on the outdoor unit. Wire coming out of the house (6) are colored red, blue, white, green brown, and yellow. Wires (4) out of the unit are colored red,green blue and white and there are 4 wire nuts. How should I match them up? Thanks. Paul
Paul, you will need to look at the indoor unit and determine which wires from outside are connected inside. let me know. more then likley they color coded it but better to be safe. also does the fan inside still run if you switch thermostat to fan ON ... Air Conditioners
I have a hunter programmable thermostat model #44155c and Im trying to wire it to my goodman furnace. Its a 7 wire system with a white,yellow,red,green,brown,blue, and orange wire. The ac works fine but the heat wont shut off. Thanks
Make sure you do not have a jumper between the red and the white. Also make sure the wire is not hanging out from behind the screws. If the heat stayes on no matter what you do. The red wire has to be touching the white somewhere. \015\012The r ... LG LSC183VMA Split System Air Conditioner
Need to change a broken blower motor in RUUD central air unit. Old central air blower motor (GE electric) was connected with brown and orange wire to 15 MHD capacitor. Another orange wire from central air unit connected to orange motor wire on capacitor. Black wire from motor (Hi Speed) connected to central air unit. Blue and red wires not connected. New motor is an AO Smith FD6000A. Has Black, brown/white, brown, blue,yellow,red, white and black wires. Need to connect to a 5 MHD capacitor. M
On the motor should be a diagram detailing the wires. brown white goes to either side of the capacitor and brown wire to other side of capacitor. hi speed goes to normally open contact on the indoor fan relay and the wire designated common on the mot ... Air Conditioners
Thermostat with 4 wires, red, green, white and blue; no yellow wire to connect to new thermostat
... Air Conditioners
Trying to hook up Honeywell RTH6350 thermostat. When turned on cool out air blows out. We only have a green, red, yellow and white wire from the old unit. Are we missing some wires? we have a heat pump.
Your Thermostat should wire as Red to Rc/Rh (if Rc/Rh are not connected you need to put a jumper between them; White to W; Green to G; and Yellow to Y on your thermostat. These will be the only wire connections that you need ... Air Conditioners
Need help wiring this theromostat. I ahve the following color wires.....Green Red Black Blue White Yellow and Orange. Need to match them to the following connections: G RC RH Y/O W/B Y1
G= Green Wire (Fan) RC= Red Wire (Power Cooling) Y1= Yellow Wire (Cooling Contactor) RH= Black Wire (Power Heating) WB= White Wire (Heating Control) YO= Orange Wire (Damper Control)Blue Wire is usually to C= Common ... Air Conditioners
Honeywell thermostat T874R 1579 Subbase Q674L 1579 has letters O W2 E G R C L Y wire to a Carrier 50NQ-024 Heat pump 1 stage cooling 2 stage Heating wire colors red blue green yellow white
... Air Conditioners