Having problems with your Air Conditioners ?
Blower motor wont stop - Carrier 38CKC036 Air Conditioner
If you are talking about the indoor blower motor, check the fan switch on your thermostat to make sure that it is in the auto position. If it is, you could possibly have a stuck contact in the thermostat or the relay in the board has stuck open, you can try turning off the power to the unit and resetting it, but I would check the thermostat first. if you have an ohm meter handy, with the power to the furnace off, pull the face off the thermostat and ohm out between r and g terminals on the thermostat, if you have continuity, you know that the thermostat has failed.
Repair Help & Product Troubleshooting for Air Conditioners
You need a second opinion or clarification ? ask it in the comment box OR you can Ask Your Own Question
Tips for a great answer:
- Please provide as much detail as possible as this will allow our members to better understand and respond to your Comment
- If you need clarification, ask it in the comment box
- It's 100% free, no registration required
Suggested Questions/Answers :
It is recommended you read all this kind of situations
Blower motor wont stop - Carrier 38CKC036 Air Conditioner
If you are talking about the indoor blower motor, check the fan switch on your thermostat to make sure that it is in the auto position. If it is, you could possibly have a stuck contact in the thermostat or the relay in the board has stuck open, you ... Carrier 38CKC036 Air Conditioner
Blower fan motor wont start on carrier package unit air conditioner I have a Carrier 50ZPA042-301TP package unit
... Air Conditioners
Fan motor on Carrier inside runs backwards - Carrier 38CKC036 Air Conditioner
Hi,\012Sometimes a motor can start to run backwards... on an indoor fan it is usually because the air inside for some reason started the fan backwards while it was off and then when power is applied it continues to run backwards... once this ha ... Carrier 38CKC036 Air Conditioner
My ac blower stays on and no cold air - Carrier 38CKC036 Air Conditioner
Problem w/condensing unit check the breaker. ... Carrier 38CKC036 Air Conditioner
Blower fan in the inside unit tries to turn on but wont. It can be turned manually and air conditioner comes on and runs fine. The " squirrel " cage spins completely freely and is not sticky or jammed. Is the motor bad or is it a run capacitor. Model number of inside unit is a49-15
\011Sound more like the cap, but if the motor is raging hot, it could be the motor, another thing it could is improper voltage although less likely. But Goodmans/ do have this weird fan relay issue were they just bite it some times. I wo ... Goodman Air Conditioners
How to install blower motor on carrier unit - Air Conditioners
... Air Conditioners
Fan motor Bad - Carrier 38CKC036 Air Conditioner
Thats like saying yep and nothing else whats your question if you say its bad replace it please clarify ... Carrier 38CKC036 Air Conditioner
No high speed on blower motor - Carrier Air Conditioners
If motor works on heat, but not on cool ,then the low speed is energized by the heat strip or control board .if the motor doesn't run in high on cool, then the fan relay or black high speed tap from the board is not being energized. usually its the f ... Carrier Air Conditioners
Air conditioner runs for a few hours and it works - it cools the house. Then it stops cooling - the fan still runs but it doesn't blow out cool air any more. It seems like it's overheating or something. It will blow out cool air if it has not been turned on in a while but once it's on too long it stops. I was told it could be the fan motor and the a/c guy changed the fan motor today but that didn't fix the problem. Now he says it might be the compressor or that I need a new system. I'm jus
The things I would check:\015\012Is the system properly charged with freon? Sytem may be overcharged.\015\012Is the compressor out on internal overload at the point of failure? If the overload isnt tripped and the compressor is having tro ... Air Conditioners
We require condenser fan motors for Interclisa Carrier package (rooftop) air conditioner model AAD 250 (1980's model) model. Air conditioner - supply voltage 380 Volts 50 Hz AC. Condenser fan motor voltage 220 V0lts 50 Hz
Hi, this is an odd voltage 380 volts. Is it a 3 phase unit? To get a 220 volt 50hz condenser fan motor, you will have to go through a refrigeration/air conditioning parts house and order this. 60hz you would have no problem finding one in stock. Carr ... Carrier Air Conditioners
My Intertherm model 018 air conditioner leaks from the a-coil the pan is not clogged or overflowing. I have had the motor replaced twice as the drip from the a-coil has shorted out the motor both times. If I remove the panel cover the leaking stops and all of the water dries up from around the fan and wires but the air conditioner doesn't cool properly with this cover removed.
This is most likely a air flow problem (not enough static pressure- duct work issues) ... Air Conditioners
Blower motor relay switch problem I have a weather maker 8000, everything works fine but blower motor wont come on, just a click, and after it does not come on the the furnace stops, is this a blower motor relay switch, and if so, where is that located to replace? thank you, scott.
Hello, if this is a electronic ignition Furnace the relay is located on the intergrated control board. The only problem is that you cannot replace only the relay on those boards, the whole board must be replaced. ... Air Conditioners
Recently replaced blower wheel and blower wheel motor mounts,that problem was solved but now fan motor for the compressor runs non stop-wont shutoff except by breaker box.also changed thermostat at the same time.have i inadvertinly placed the wrong wire terminal in the wrong recepticle in either the blower motor or thermostat? If so,which one and where?How can it be fixed?The unit is a 1973 coleman evcon.
First question first, NO! this is a simple problem and a common one to fix, just change out the outside contactor coil, the contactor has a thin layer of silver on them to prevent them from arching and sticking together, over time this thin layer b ... Air Conditioners
Replaced the blower motor on a Carrier a/c unit x421892 after motor seized and tripped breaker. New motor runs fine but runs continuosly when put in the auto position. The motor still runs even when thermostat is turned off. Breaker must be off to stop blower motor. Any suggestions on how to fix this problem?
Hello The new motor sounds HOT wired.It must have one leg connected to the blower relay.If it is off the relay(correctly) ,the relay is stuck/welded and should be replaced.In the blower unit. ... Carrier 38CKC036 Air Conditioner
Blower motor stopped, there is a medium-loud ''electric buzz'' sound every minute or so as if trying to start the blower motor. Could be relay switch. Last week, I extracted the entire motor and fan assembly (the one in the bottom of the furnace that drives the air through the house duct system). The motor was pretty filthy, so I took the entire thing apart an blew out all the dust, cleaned up the motor, Zoom oiled the bearing assemblies at each end, put it all back together. Started up and ran
You have a bad "starting capacitor" .. the capacitor is used to get the motor to start in the correct direction .. when its bad the motor doesnt know which way to turn so it just sits there buzzing until it gets hot .. that trips a thermal breaker in ... Bryant Air Conditioners
Carrier 48NMX042 IFM wont stop, condenser fan motor and compressor wont run
Ok first thing is it sounds like a wiring problem. So first step is to make sure the thermostat is properly connected. Which... the main thing here is there needs to be 24v dc power coming from your control board (transformer) going to the thermostat ... Carrier Air Conditioners
Hi, just replaced the capacitor thinking that would solve the problem but it appears it did not. The motor outside would kick on the unit inside would kick on but the blower motor inside works sometimes and wont other times. Basically, the unit will work just fine all day then we notice the house is getting warm, check the inside unit and everything is running fine but the blower motor is not circulating the air. I have a goodman a30-10 unit. I read where some people said the relay could be bad
Turn off the power to the air handler(indoor unit). Remove the access panel. From the motor,trace the wires back to the fan relay. One wire will probably trace back to the incoming power terminal. The other is the fan relay. It could be intermittent ... Air Conditioners
Carrier oil furnace model 58BMA155-20(FORCED HOT AIR)i had changed the blower motor & honeywell st9103a128 fan control board.now the blower motor won't shut off until the breaker is turned off.i disconnected the thermostat an it's still the sameway.fan control board was replaced with a honeywell st9103a1002 board.blower motor was replaced with a 3/4 hp universal motor.i also have central a/c.
To have your work constantly the fan or the board has a problem communicating with the new fan or if outdoor ... Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
My goodman cental air system is having problems. First, the blower inside (furnace) keeps running for hrs after the outside condensor shuts down. Now, the condenser blower motor wont operate at full speed. I have replaced the motor and capasitor with no changes. Can anyone help with these problems???
The cause of your indoor fan running all the time or for long time after your heat pump has stopped heating is the fan delay relay. It has welded its internal contacts together. If you take off the side below the control panel, the fan delay relay ... Goodman CLQ36AR49 Air Conditioner
Air conditioner blower fan wont turn off - Air Conditioners
If this is central AC unit check the fan motor to see if it will try to run. If the motor tries to run it may be capacitor easy to change. If not posible fan relay. Please keep in touch and I will help you with this problem. Rus Need more info pleas ... Air Conditioners
I have a sunbeam 12000 btu window unit air conditioner. I can't seem to change the fan speed when it is in cool mode. When I put it on fan only it blows extremely cold air and i can change the fan speed. When i press the power button it stops blowing but it sounds like the motor is still running and I must unplug it to get it to stop.
Sounds like the switch is wired wrong.\015\012When you put the switch on fan only the compressor should not run at all, therefore their shouldn't be any cold air.\015\012Check the switch to see if it's wired right. ... GE Profile ASM10AA Air Conditioner
Air conditioner blower motor not kicking on - Air Conditioners
Either motor is bad or contactor is not suppling power to motor, but chech panel for blower, there is a switch that must be pushed in or it will not operate ... Air Conditioners
Furnace is a York Model#p4ugd12n09001a probably installed around 1991. The air condition was working fine. couple of days ago nothing was working. Blower wont tun on, air conditioning unit wont turn on. I did have the fan on the on position on the thermostat so it was always on until it stopped.
Probably a bad low voltage transformer. ... Air Conditioners
Re: Kenmore Plasmaire air conditioner; suddenly stopped working during night. Motor will initially turn on but no air coming through, then will stop
Most likely you have a bad fan,did you have a storm or lighting strike or power drop / outage . \015\012 These type of things can cause trouble with a weak electrical part - not know the age of the Unit - you claim it happen in the middle of ... Air Conditioners
Hello, We bought a Perry Home in Georgetown TX last March and it is still under its two year warranty. Our air conditioner stopped cooling today. It has been working well for over 1 year. We came home from work and the temperature is 86F inside and climbing. My wife left the house at noon and the temp was 76F (where we keep the thermostat in the summer). The Air conditioner outside unit's fan is operating and no noise. The inside blower is running normal - no problem. The model number on the o
You have a 10 year warranty on your AC. Call a Goodman rep and have it serviced. It will probably be a bad compressor capacitor. Bad wire or no refrigerant. ... Goodman Air Conditioners